- 15. 11. 2021
In conjunction with the General Directorate of DESKI in Bagbasi Neighborhood, physical water loss leak detection works were done. On the approximately 10-kilometer pipeline, three leak points were detected in the network using two Gutermann brand data collectors Alpha, 23 signal repeater repeaters and 32 Zonescan 820 model noise recorder correlators. The leak points identified through the system were confirmed by the institutional authorities with the Gutermann Aquascope 550 model acoustic listening microphone. Excavation operations were carried out and the leaks were repaired. We would like to thank my teammates for their support.